Bamo Water Hardness Monitor BAMOSOFT Smart safely the water quality produced by the softener. It alarms (LED and relay output) when the softened water hardness is 10% or over the hardness of raw water.
BAMOSOFT Smart gives an alarm as well as brine (leakage) is detected at softener outlet and if system integrity is not in conformity (solenoïd valves, electrode effectiveness). In the event of a fault, the controller issues an alarm signal to warn the user of the maintenance to operate (See LED-Status and Displays)
Bamo Water Hardness Monitor Example :
– Raw water inlet = hardness of 300 ppm CaCO₃ – System is alarming if softened water hardness > 30 ppm CaCO₃
BAMOSOFT comprises two solenoid valves that successively pass raw water then softened water on a specific ion electrode Ca⁺⁺ / Mg⁺⁺ . The specific hardware carries out the analysis of ionic activities, compares data and proceed to diagnostic routines.
The device then delivers the following information: correct measurement, alarm, defective valve, brine leakage, etc. Samples are wasted to drain after each analysis. When the first cycles of measurement are stable, BAMOSOFT operates a control each 15 min. Measuring cycle may be started by an external signal (pulse from a counter or an external contact).
LED Status displays
According the message, LEDs are alight or flashing.
- LED 1 (green):
- Alight: Measurement is alright
- Flashing: Monitoring cycle is running
- LED 2 (red):
- Alight: Softened water hardness > 10% of raw water hardness
- Flashing: Brine leakage detected in softened water
- LED 3 (red):
- Alight: Electrode replacement required
- Flashing: Leakage of a solenoid valve
- When the 3 LED are flashing together: Electrode is not properly mounted.
- Fit any water softener
- In-line monitoring
- Alarm set up at 10% of raw water hardness
- Automatic diagnostic of complete system
Control and monitoring of water quality between inlet and outlet of the softener.
Bamo Water Hardness Monitor Specification
|Ambient temperature||+5 … +50 °C|
|% H.R.||30 … 80 %|
|Power Unit (included)||100 … 240 V AC; 50/60 Hz; 0.2 A|
|Power supplied||15 V DC; approx. 4 W|
|Relay output||N.C. contact; max. 24 V DC; 0.5 A; Alarm/ Fault on Threshold, Brine, Electrode, Solenoid valve|
|Raw water inlet||By-pass with fitting for PA tubing|
|Inlet for softened water||O.D..4 mm,; I.D. 2 mm, necessary filtration unit (<0.1 mm)|
|Pressure limits for raw water||Min. 1 bar; Max. 10 bar (raw & softened waters)|
|Drain outlet||PA tubing; O.D. 8 mm; atmospheric pressure|
|Raw water quality||Drinkable water, free of grease, oil and brine, biol.: < 5000 KVE /ml|
|Raw water hardness limits||2 … 100 °f (20 to 1000 ppm CaCO₃)|
|Electrode check up||Automatic test with indication of low efficiency|
|External cycling switch||Pulse limit: >0.5 s|
|Dimensions||Wall mount cabinet: 120 x 80 x 55 mm (Overall: 250x220x100 mm)|
Download Data Sheet: Water Hardness Monitor BAMOSOFT Smart
You must be logged in to post a comment.